A steel pipe collar is internally lined with Intumescent material that fits around plastic pipework. The collar is hinged for ease of fit and secured with a clip fastener.
Attachment to the wall or underside of the floor slab is by 6mm anchors fixed through integral steel lugs. Fix to plasterboard ceilings/walls using hollow wall metal anchors. Such as Fixfirm M5 Ref A661-235.
Suitable for use where plastic pipes pass through both walls or floor slabs. In a fire the Intumescent expands and closes the hole left by the collapsing pipe, so retaining the integrity of the structure. Ratings available 2, 3 and 4 hours.
Features and Benefits
Easy to install on initial build or retrofitting
Available in a wide range of sizes
Finished in red for easy identification
Contact Us for Steel Pipe Collar
Undo Clip and place collar around the pipe, close firmly by shutting the clip.
Slide the collar along the pipe to form a seal with the wall or slab. FireSure® Intumescent Mastic should be used as gasket material to take up any imperfections between the collar flange and the wall or floor slab.
Preferred fixings should be by 6mm anchors or in the case of studded walls/plasterboard ceilings by cavity fixings such as Fixfirm hollow wall metal anchors Ref A661-235.
Now tested on 103mmØ 1.6mm thin wall ducting uncapped/uncapped in 100mm stud partitioning to BS EN 1363-1: 2012 and BS EN 1366-3: 2009. 1 each side to 132+ minutes – no failure. Tested To BS: 476 Part 20-23 - BSEN 1363-1: 2012 - BSEN 1366-3: 2009 Health and Safety - No reportable hazard to health
|IPC038||Up to 40||Up to 240||6 – FEI/F97033a|
|IPC055||55||Up to 240||6 - FEI/F97033a|
|IPC068||68||Up To 240||6 – FEI/97033a|
|IPC082||82||Up to 240||6 - FEI/F97033a|
|IPC110||110||Up to 240||6 - FEI/F97033a|
|IPC160||160||Up to 240||4 - FEI/F02047a|